top of page
Fhase Protection Relay
Characteristics of Function
Phase reverse protection: It is a safeguard acting immediately, which protects L1, L2, and L3 three phase against wrong connection sequence. In this case, the Yellow indicator light will be lighted.
Phase loss protection: It means that any phase occurs phase loss when the protected circuit is in running or stopping status. In this case, the red indicator light will be lighted and be priority.
Voltage imbalance protection: While a protection of voltage imbalance rate >8%, the imbalance of three phase voltage will affect the safe running of the equipment. In this case that there is a phase losing, the red indicator light will be lighted and be priority.
Anti-lightning, anti-surge function: built-in lightning protection, anti-surge protection circuit to maximize the protection of your electrical equipment.
เครื่องควบคุมอุณหภูมิ / ความชื้น
Temperature / Humidity
Characteristics of Performance
There is no requirement for connecting method when it is used in protection of motor.
The protection functions of relay don’t be affected by current intensity of circuit or load, impulse current, imbalance current and load characteristic.
The relay could long term work under full capability and full climate. Power consumption is lower than 2W.
This product measures up GB/T 14048.1-2000 、GB14048.5-2001
The EMC of the product measures up the limits and methods of measurement of radio disturbance characteristics of GB4343-1995.
If the connection of L1, L2 and L3 phases are right, the green light of the relay illuminates and the relay closes. If they are wrong, the Yellow light of the relay illuminates. Exchanging any two of them, the relay will accept the phase sequence and begin to work normally. In this case that there occurs Yellow light illuminated and relay unclosed after the protected equipment works normally, it should be a wrong connection of external circuit. The relay has a function of protection against wrong connection.
L1, L2, L3 three-phase voltage is not measured > 15%, the red light, the relay release; voltage rose to <10% recovery, the green light, and closed relay.
L1、L2、L3 any phase occurs phase loss, the red light, the relay release; The restoration of normal voltage, the green light, and closed relay.
bottom of page